Hot Tub Electrical Installation Hookup GFCI Load 1 input wire goes to load 1 terminal, load 2 input wire goes to load 2 wire. For the output section of the GFCI breaker, the load 1 output wire goes to line 1 of the spa and the load 2 output wire goes to line 2 of the spa. The load neutral output provides the 120v difference between the Line wires and is connected to the Neutral White terminal on the circuit board, spa pack as directed by manufacturer instructions. Looking at the bottom of the GFCI, the incoming neutral wire electrical - How to wire a 240V disconnect panel for spa On 2P 15A to 50A the GFI breaker will work with or without a load neutral wire. However, if there is no load neutral wire the breaker neutral (white curly wire) must still be connected to the panel neutral. On 2P 60A and all 3P (QO only) there is no load neutral wire connection on the breaker. Again the breaker neutral (white curly wire) must be connected to the panel neutral. Related searches for 220v gfci breaker wiring diagram 220 gfci breaker wiringwiring 2 pole gfci breaker3 prong 220v wiring diagramsiemens gfci breaker wiring diagram240 volt gfci wiring120v gfci breaker wiring diagram220 volt gfci breakerhow to install gfci circuit breaker
Downloads 220V GFCI BREAKER WIRING DIAGRAM Wiring Diagram How do you find 220V GFCI BREAKER WIRING DIAGRAM? What are the two types of 220V GFCI BREAKER WIRING DIAGRAM? What is wiring assembly 220V GFCI BREAKER WIRING DIAGRAM? How do you draw a 220V GFCI BREAKER WIRING DIAGRAM?